Make sure you have properly installed your contact closure sensor bridge before continuing with the web configuration.
Sign in to my.senseware.co to configure your sensor bridge. You can set up the bridge under the module configuration tab on the installation page. The data is directly available via data forwards or the Senseware Dashboard.
On the module configuration tab, you can decide whether the LED related to each channel will turn on with each contact or not. You can also change in which mode the bridge is operating, depending on the type of equipment you are connecting to:
Bridge Voltage Source
External Voltage Source
Pulse to ground
When the bridge is connected to a Node on battery, the LED setting is automatically set to 'Off' to optimize battery life.
You can configure the bridge to send data immediately in case of state change to be alerted instantaneously that an event occurred. To do that, turn on the 'State Change Notification' setting.
The conversion functions 'On', 'Water Leak' and 'Overflow' are triggered when the contact is closed. The conversion function 'Open/Closed' shows Open when the contact is open and Closed when the contact is closed.